Swivel Photoelectric Switches for Lightingcontrol UL773A
|FOB Price:||Get Latest Price|
|Min. Order:||1 Piece|
|Payment Terms:||L/C, T/T, D/P, Paypal|
- Model NO.: 104
- Output Signal Type: Switching Type
- Material: Plastic
- IP Rating: IP65
- Customized: Customized
- Transport Package: Carton
- Origin: China
- Type: Diffuse Reflection Type Photoelectric Sensor
- Production Process: Integration
- Feature: SemiConductor
- Certification: UL
- Trademark: JL or Can be customized
- Specification: 1pcs/Box, 100box/Carton
- HS Code: 85365000
|Rated Voltage||100-120VAC,208-277VAC 50/60Hz|
|Rated Loading||1800W Tungsten 1100VA ballast|
|Ambient Temperature||-40ºC ~ +70ºC|
The photoelectric switch JL-104 is applicable to control the street lighting, passage lighting and
doorway lighting automatically in accordance with the ambient lighting level.
This product is designed on the basis of electrical heating structure that provides time delay over
30 seconds to avoid redundant switching against spotlight or lightning during the night time. A
temperature compensator system provides consistent performance regardless of the ambient
JL-104 has a gathered swivel with the sensor/switch body for convenient direction adjustment
after installation. Additional swivel is also available for further adjustment.
This product is certified to the Standard for Non-industrial Photoelectric Switches for Lighting
Control UL773A and applicable Canadian Standards.
° Time Delay 30~120 seconds
° Temperature Compensated
°Screw Thread & Zinc Alloy Nut
°Additional Swivel Available
|Item No.||JL- 104A/JL- 104B|
|Rated Voltage||100-120VAC, 208-277VAC|
|Rated Loadings||1 8 0 0 W T u n g s t e n|
1 1 0 0 V A B a l l a s t
|On-Off Levels||10~20Lx On (Dusk)|
30~60Lx Off (Dawn)
|Ambient Temp||-40ºC ~ +70ºC|
|Body Meas.||Body: 88(L)x 32(Dia.)mm; Stem:27(Ext.)mm; 180o|
|Swivel Meas.||85(L) x 36(Dia. Max.)mm; 200o|
|Leads Length||150mm or Customer request; AWM3321, AWG#16|
|Approx. Weight||58g (Body); 22g (Swivel)|
place screw thread of the SWITCH in knockout hole and fasten with rubber
gasket and Zinc alloy lock-nut.
Wire according to the diagram in right hand.
Do not install the switch with the Photocell facing artificial or reflected light.
This will cause the unit to cycle on and off at night.